- Meet The 2022 Florida Statutes - Chapter 509.211 Safety Regulations
- Engineer Specification Documents
- Product Literature
- User Installation
- Select a Gas Solenoid Valve
- Ancillary Products
509.211 Safety regulations
(4) Requires that every enclosed space or room that contains a boiler regulated under chapter 554 which is fired by the direct application of energy from the combustion of fuels and that is located in any portion of a public lodging establishment that also contains sleeping rooms shall be equipped with one or more carbon monoxide sensor devices that bear the label of a nationally recognized testing laboratory and have been tested and listed as complying with the most recent Underwriters Laboratories, Inc., Standard 2034, or its equivalent, unless it is determined that carbon monoxide hazards have otherwise been adequately mitigated as determined by the division. Such devices shall be integrated with the public lodging establishment’s fire detection system. CO METERS by set to shut boiler off and 35ppm and Must have a Manual Reset.
AGS supply gas solenoid valves ranging from 1/2″ to 6″.
AGS Gas Solenoid Valve Selector Sheet