‘Each boiler room containing one or more boilers from which carbon monoxide can be produced shall be equipped with a carbon monoxide detector with a manual reset.
(1) The carbon monoxide detector and boiler(s) shall be interlocked to disable the burners when the measured level of CO rises above 50ppm.
(2) The carbon monoxide detector shall disable the burners upon loss of power to the detector.
(3) The carbon monoxide detector shall be calibrated in accordance with the manufacturer’s recommendations or every eighteen months after installation of the detector. A record of calibration shall be posted at or near the boiler, or be readily accessible to an inspector.
(4) The requirements in this subsection apply to boiler rooms in which need installations or re-installations of one or more boilers are completed on or after September 1, 2020.’
AGS Mini Merlin CH4CO User & Installation Guide
AGSCH4CO Mini Merlin Product Datasheet
AGSLPGCO Mini Merlin Product Datasheet
AGS Mini Merlin Brochure
AGS Mini Merlin Positional Diagram
**OTHER SIZES ARE AVAILABLE UPON REQUEST. CONTACT AMERICAN GAS SAFETY OR YOUR LOCAL REPRESENTATIVE FOR FURTHER INFORMATION.